Light Efficient Design is dedicated to providing the type of products that you demand. Proper certifications, such as M79, Lighting Facts, UL and ultimately Energy Star, are top priorities for Light Efficient Design. These labels instill confidence in the quality of their products. More and more of their products carry certifications, and ultimately most will be certified. Some of Light Efficient Designs products, in what we believe to be one of the broadest assortment of LED lights anywhere, might appear to be similar to many competitors products but we can assure you that the intrinsics, which you cannot see, have been designed to give you the performance and longevity that you expect from LED products, but do not always get in this vast unknown supplier industry.
Here is Light Efficient Design's item LED-8088E(XX)-G4, suitable for totally enclosed post top, shoe box and other typical HID fixtures, fully encapsulated, Type V beam angle retrofit LED bulbs. Part number LED-8088E(XX)-G4, a replacement for LED-8088E(XX), consumes just 50 watts of 120 to 277 volt 60 Hz energy and generates a comparable light output to your 175 watt Metal Halide (MH) or High Pressure Sodium (HPS) bulb. This non-dimmable LED light bulb, an LED Site, Roadway or Wallpack lighting retrofit option, will produce 6,915-7,250 Lumens of light output, is available in 3000K Warm White, 4000K Cool White and 5000K Daylight, has a CRI of 80 and an average rated life of up to 50,000 hours.
These LED bulbs have the screw-in E26 Medium base that easily integrates energy saving LED technology into your standard site lighting, roadway or wall pack lighting format. This LED lighting retrofit has an aluminum/acrylic construction. The physical dimensions of the Light Efficient Design LED retrofit are 8.1 inches long by 3.3 inches wide. These NON-dimmable LED retrofit bulbs carry a 5 Year Limited Warranty.
The LED-8088E(XX)-G4, 50 watt LED retrofit lamp has been designed to retrofit existing Metal Halide or HPS installations, thereby reducing maintenance and energy expenditures in residential, commercial, retail displays, hotel, motel and resort applications and as an energy saving light source for new fixtures and installations. Please NOTE: When retrofitting LED to an HID fixture, the ballast must be by-passed or removed from the fixture. Additionally, by-passing the ballast will insure no RFI interference.